Please note, the order volume has been updated. This is due to package and minimum order quantities.
Please note, the order volume has been updated to. This is due to package and minimum order quantities.
What is an EJ?
An engineering judgment, or EJ as they are commonly known, is a drawing or group of drawings typically generated by a firestop manufacturer for a customer’s jobsite-specific application. They are recommended as a solution when a customer’s jobsite condition deviates from a tested firestop design/system.
What is their purpose?
Contractors consistently encounter unique jobsite conditions requiring new penetrations through fire-rated assemblies regardless of how many firestop systems are tested and approved by third-party testing agencies. Custom drawings are sometimes needed in order to provide the most comprehensive fire protection solution for an entire project to account for these unique applications for which a tested and approved system does not already exist.
How are these drawings created?
Per International Firestop Counsel (IFC) guidelines, engineering judgments are firestop designs created by qualified personnel based off of third-party tested and approved systems. These designs are in accordance with the recommended IFC guidelines for evaluating firestop system engineering judgments.
Engineering Judgments at Hilti
Firestop systems are designed and installed to impede the passage of fire, and toxic smoke, with some systems designed to also restrict water and sound, through construction openings in fire-rated assemblies. These systems are required by all Model Building Codes to be tested and rated as part of an assembly in accordance with ASTM E-814, ASTM E-1966, ASTM E-2307, or CAN/cUL 8115 and/or other applicable fire testing standards (UL 1479/UL 2079). The International Building Code (IBC) justifies the use of engineering judgments as referenced under sections 703.2 Fire Resistance Ratings and 703.3 Alternative Methods for Determining Fire Resistance, IBC 2012. The testing and rating process ensures that each specifically designed system will maintain or exceed the hourly fire rating, as tested, for which it was approved.
The IFC guidelines recommend that tested systems be used in lieu of engineering judgments when available and that engineering judgments be based on previously tested systems. Additionally, engineering judgments should only be issued by qualified technical personnel.
All project and application-specific information, such as the penetration type and size as well as the location of the penetrating item, must appear on the drawing. Engineering judgments must only be issued for a single job and should not be transferred to another job without review by the entity who issued the EJ of all aspects of that job’s specifications to determine whether or not the EJs are applicable to the new project.
Key Fundamental Guidelines
Basic EJ Presentation Requirements
To see account specific prices and content, please choose appropriate account.